Estimated reading time: 0 minutes, 59 seconds
I recently returned to a kitchen remodeling project to figure out why the a counter outlet stopped working. I traced the power back under the crawl space to a junction box with a GFCI outlet that would not reset and had a flashing red LED in it. I turned it into a junction box and left the outlet un-energized as a cover plate of sorts until I can get back up there. We do not have non-working outlets in our projects.
Looking it up I realized that it was a failed GFCI outlet. It was nice to have the flashing light indicator. Are they becoming more temperamental, or is it just me?
Your comments are welcome. To ask questions or get more information about proactive home care, click here to email me directly, or call 208-639-1808
If you or someone you know could potentially use our services, or just wants to speak to a trustworthy contractor, please contact me. You’ll be glad you did.